For tunnel ventilation the building must be sealed for ventilation to be effective. All roof vents, chimneys, side vents, windows, doors, and openings other than the air inlet area opposite of the fan wall must be closed.
Buildings with open ceilings require baffles. Baffles should be equally spaced throughout the length of the building and hung as low as possible without effecting the daily routine of machinery. Baffles ensure that the air movement maintains the velocity.
Evaporative cooling systems for the air inlet end of tunnel ventilation system are frequently recommended. Air intake is determined by the number of fans.
During winter fewer fans are required to remove gas, keep air fresh, and humidity low. The winter rate should be approximately 50 to 100 cfm per cow.
For adequate ventilation, SCHAEFER products best suited are:
SCHAEFER's 57" Cone Exhaust Fans
5-wing or 3-wing, high volume or high efficiency configuration with 1.5 or 2 hp
Designed to fit side-by-side and maximize the number of fans that can be installed in with 12’, 18’ and 24’ post spacings.
Easy maintenance, with easy belt replacement and optional Remote Lubricating System
Please contact us for more information on tunnel or cross ventilation systems for your buildings.